The Direct Storage Style Rainwater Harvesting System shall be designed to collect rainwater in an outside storage tank (supplied by others). Water will be re-pressurized from the collection tank to the points of use by (2) sump pumps through the initial strainer filtration to the interior storage tank. Water will then be recirculated in this tank for chlorination and disinfection. The booster pump pack will then pump through bag filters and the water will be injected with dye. When not feeding the points of use, the recirculation pump will recirculate the interior storage tank to keep the water sanitized. The Rainwater Harvesting System shall be controlled via a common PLC driven control panel with touch screen operator interface.
2.0 EQUIPMENT DESCRIPTION for Rainwater Harvesting System
Interior Water Storage Tank
1000 gallon capacity
White polypropylene construction, thermally formed sidewalls and butt-welded construction with extrusion welded exterior and triple bead welded interior
Tank shall have the following welded fittings: rainwater inlet, vent, level control mount, city water inlet, recirculation return, pump suction flanges, and drain
Integrally welded cover with 24” access man-way
Non-metallic spray ball assembly on recirculation return line
Level Transmitter (1 for exterior tank and 1 for interior tank)
Continuous, non-contact level indication
8”-26.2ft operating range
+/- 0.2% of span accuracy in air
1 mm resolution
PVDF transducer material, NEMA 4X housing
4-20mA two-wire output
Distribution Pump booster pack SyncroFlo booster pump pack TS43V73VFD rated to 70gpm @155 TDH for each pump. Pack includes flow sensor and pressure transducers, central control panel with VFD’s, hydropneumatic tank shipped loose, spare parts and all equipment mounted and wired, factory tested prior to shipment on one complete skid.
Dye Storage Tank
One-piece construction rotationally molded of linear medium or high-density polyethylene.
Finished surface of tank shall be free as commercially practicable from visual defect such as foreign inclusions, air bubbles, pinholes, craters, crazing and cracking that will impair the serviceability of the tank.
The tolerance of the outside diameter including out of roundness shall be +/- 3%.
Tank shall be 55 gallon capacity, vertical cylindrical construction with dimensions of 22” diameter x 36” tall.
Tank shall have 1/2” thick bolt down polypropylene cover and include factory mounting of metering pump
Include single point float level control for reagent low level alarm
Electronic Dye Metering Pump
Automatic control with analog input
Built-in circuit protection against voltage and current upsets
Wetted parts: PVC, Ceramic, and Teflon
Supplied with multi-function discharge valve, suction strainer and injection check valve
Pulsatron model LPA2MA-VTC1
Flow Sensor for Dye Injection Control
Paddle Wheel Style Sensor
Flow Rate Range 1-20ft/s
Linearity of +/-1% of full range
Repeatability of +/-0.5% of full range
Signet model P51530P0
Bag Filter (2 units 100 micron, 2 units 50 micron)
T304SS construction, sized for #2 filter bag
Swing bolt lid closure
130 gpm flow through capacity
One case of 100 micron and one case of 50 micron bag filters included
55 gal. Dry powder make-up and metering chlorine injector with tank, mixer, controls for concentration make-up and metering pump.
Rosemouny free chlorine monitor with sensor, analyzer, flow contrl and continous pH injection.
Plumbing and valves to be sch.80 PVC with Viton seals where applicable. Asahi brand.
Hellan fluid strainer simplex 2” size with stainless steel 1/16” perforations strainers and carbon steel housing.
Central system control panel containing the following:
Three phase disconnect switch to automatically cut power to the panel for servicing. Provided with lockout capabilities.
Motor protectors for recirculation pumps
Siemens series programmable logic controller (PLC) to contain ladder logic to operate the entire system.
Siemens graphic display package including touch screen for each electric device in the system to indicate its operating status.
NEMA 4 electrical rating
UL panel labeling required
Adjustable alarm horn with silence button
All required controls and accessories for complete system operation
Rainwater Harvesting System components other than storage tank level transmitter, storage tank and booster pump pack to be factory mounted and plumbed on common epoxy coated carbon steel skid.
Electrical conduit shall be corrosion resistant PVC with PolyTuff flexible conduit as manufactured by Hubbell.
Rainwater Harvesting System manufacturer shall provide two days of site assistance to cover start-up and training.
Manufacturer shall include a Certificate of Insurance with their submittal approving that they are insured as a supplier and manufacturer of such systems.
The Rainwater Harvesting System Manufacturer shall be capable of providing a maintenance agreement with the system owner should the owner wish to enter into such an agreement.
The Cistern Storage Rainwater Purification Systems include filtration and sanitization equipment and controls to filter 56,000 gallon rainwater cistern. It shall be factory skid-mounted including modularization and pre-plumbing and wiring...Read More
The Rainwater Recovery Systems shall be designed to collect rainwater in (2) 30,000 gallon storage tank (supplied by others). Water will be re-pressurized from the collection tank to the points of use by (2) booster pumps. The booster pumps will pump through bag filters and a 254nm UV for sanitization on the Reclamation water skid. When not feeding the points of use, the pumps will recirculate to the storage tank to keep the water sanitized. Water for flushing fixtures will also be injected with dye. A 55-gallon molded HDPE tank is included with a solenoid driven meter pump...Read More
The Direct Storage Rainwater Recycling Systems for University shall be designed to collect rainwater in a 4,000 gallon storage tank. Collected water will re-pressurized via one of two pumps to output water at a rate of 35 gpm @ 40psi to the irrigation system. When not feeding the irrigation system, one of the pumps shall recirculate the holding tank through a bank of bag filters and a 254 nm UV for sanitization. The pumps will automatically alternate with each cycle. The system shall be controlled via a common PLC driven control panel with touch screen operator interface.Read More